快点嘛人家痒8:30a.m. - 9:30 a.m.
Kevin, Cameron, Brent, Jeff, Hans, John, Michael, Emmanuelle,
Jeff will issue the designs for bidding on September 11, 2009, and will allow 2 weeks for pricing.Once all bids are received, coordination between systems will take place.
Cameron identified the pump and tank location, but needs to provide schematic drawings in order to have an accurate cost estimate.
On Site Waste Water System:
The current septic was designed for peak flow with infiltrators adequate for a 6-bedroom house (2 people per bedroom). The permit was issued for a 2-chamber 1,250 gallon tank. A 1,500 gallon tank would have been preferable, but since the permit has already been issued, an additional tank upstream should not be needed. Once the leach field is repaired and topsoil added it should be largely sufficient.John will apply for a repair permit with an experimental component for the wetlands.
The wetland will be about 480 to 520 square feet.A standard pump, using less than one hp will be placed after the wetland to pump water for irrigation
1. All drawings should be sent to Jeff labeled as Design for Bid, dated September 11, 2009, and paged appropriately, in addition to company logos.
2. Cameron will provide the pump electrical specs to Brent. Cameron and Lisa will provide water catchment schematic drawings asap.
3. John will provide the electrical specs of the pump he is intending to use to Brent.
4. Michael, Lisa and Emmanuelle will review the current aquaculture tank design and provide a cost estimate within the next two weeks.